1. System introduction
The standard configuration of the system is two-way AC mains 380V input, with mechanical interlock device;
24 rectifier modules are equipped as standard, each module has a capacity of 240V / 50A (15kw), a total capacity of 240V / 1200A (360kw), and the maximum capacity of 240 system can reach 240V / 1600A (480kw);
It is composed of AC distribution panel, rectifier panel and DC panel.
2. Main functions
Replace UPS uninterruptible power supply system (above 200KVA) or new data center machine room and communication core network machine room power supply system;
According to the user's demand, ATS automatic transfer switch can be customized for two-way AC mains power input;
According to user's demand, DC output fuse, specification, size and brand can be customized;
The number of rectifier modules is configured according to the load of the user's machine room, which is convenient for expansion.
3. Application scenario
IDC data center, communication core network machine room, telephone office, transmission trunk line, exchange office, government agency, cultural media, transportation, energy, hospital and other fields
4. Quality service
According to the needs of users, the UPS system shall be transformed and replaced, and the site survey and design shall be carried out, and the reasonable transformation scheme shall be formulated;
According to the user's needs, the new communication room, field survey and design, and develop a reasonable new 240 system plan;
Organize 240 power system training.